Views: 4 Author: Site Editor Publish Time: 2022-05-07 Origin: Site
What are the requirements for the installation position of compressor units?
There should be enough space outside the cold room around the compressor unit for heat dissipation, ventilation and routine maintenance.
The distance between the back of the compressor unit and the wall shall not be less than 30cm, and the base of the compressor unit shall be more than 30cm above the ground to prevent the corrosion of the unit by ground water.
A space of more than 50cm must be set aside before and after the compressor unit to avoid blocking the wind path in and out of the unit. Especially when multiple units are installed together, hot air can be avoided from interfering with each other, resulting in airflow short circuit, thus affecting the heat dissipation effect.